Conditions of Installation
I. Ceilings are delivered from the factory in sealed cardboard cartons. Please handle cartons with care.
II. Ceilings can only be installed in sealed finished buildings that are clean and free of dust. If ceiling cartons are subject to cold/freezing conditions it is most important that they rest for 24 hours in a warm environment before opening.
III. Barrisol ceilings require little maintenance, a range of cleaning products are available to suit your ceiling finish.
IV. The ceilings are custom made in our factory, adaptation can be necessary during installation therefore it is imperative that only authorized factory trained installers perform installation and dismantling of Barrisol ceilings in accordance with their technical training.
V. In the case of removing a Barrisol ceiling :
- Heat the ceiling using the hot air generator.
- Gently pick the harpoon from the track with special Barrisol removal tool and spatula.
- Let the sheet cool before folding and packing.
- Use protective film between layers.
VI. Ceilings installation in new buildings under construction, can only be performed in sealed, dry and dust free areas.
- The plenum must be 100% airtight.
- Insulation materials installed in the plenum will have a minimum fire classification M1(non flammable)
- Roller blind boxes must be airtight.
VII. Ceiling installation in existing buildings does not require the removal of furniture; however it is advisable smaller items are removed for safety and that any furniture is covered for protection.
Directional embedded spotlights are generally compatible with BARRISOL. When the diffused heat is greater that 50°C, it is obligatory to place an insulating ring between the rose of the spot and the BARRISOL sheet.
The power of the spots should not be higher than 50W. Spots that transmit more than 60°C to the metallic rose are not compatible with BARRISOL ceilings, even equipped with insulating rings.
IX. Lighting transformers are generally fixed directly to the existing ceiling or on the wall. The Barrispot is formed to receive the transformer which can be reached by hand without taking down the ceiling.
Mechanical ventilation must be adjusted to ensure that air inlet and air extraction is balanced.
X. Keep sharp objects clear of your Barrisol ceiling, handle ceilings with care.
XI. We are ready to assist you if you have engineering or other problems, please contact us immediately.